John Drake Services, Inc.
1427 E. 68th Street
Long Beach, CA 90805
Please use the following links for the subjects on this page:
electricity from the sun by John Drake II | home
About Us | About this website. | Getting Started | Solar Panels / Photovoltaic Modules - Read Before You Buy | Make A Plan | PV System Layout and Parts | Start with the loads you are going to operate | Battery Types and Sizing | Battery Safety | Battery Charging Voltages and Temperature | Battery Trouble Shooting | Charging Batteries - You can't have everything. | Battery State of Charge and Measurement | Safety Devices Fuses and Circuit Breakers | Series & Parallel Wiring | Wiring and Power Distribution Connections | Photovolatic Module Specifications - Real or a Pipe Dream | Photovoltaic module solar panel location and positioning | Photovoltaic Module and Solar Panel Information | Charge Controller Types | Wire and Cable Types | Wiring - Doing it Right | Connections for Wiring | Voltage Drop - Wire Loss, What are they? | Outdoor Connections | Wire loss - Voltage drop charts | D.C. to A.C. Inverters | Low Voltage D.C. Lighting & Color Temperature of Light | Battery System Monitoring | Dont fool yourself - Spending your money wisely. | Solar Converters GS-1AC | Linear Current Boosters for Water Pumping | Utility Grid Intertie Systems | Solar Insolation Chart | More Information | Alternative Energy Expectations | Power Needs Worksheet | Reference Sources | Contact Us
Photovoltaic module solar panel location and positioning
Proper location and set up of photovoltaics modules is
paramount to getting the most wattage from your system.
Try to locate you solar panels as close to the battery(s)
This will reduce the voltage loss which is incurred when
using long wire runs.
If you cannot mount the modules close to the batteries
you have two options.
The first, and nowadays the most expensive, is to use
very heavy wire to minimize voltage drop.
The following link will take you to our page showing wire
gauge recommendations for the incoming wires from
your photovoltaic modules:
Another option would be to wire your modules in series
or series/parallel to increase the output voltage.
Then you would use a Maximum Power Point Tracking
charge controller to bring down the incoming voltage to
the charging voltage of your system.
Many years ago a customer called about a system they
installed for the U.S.G.S. in Nevada.
They said the batteries were not charging, even in full
The photovoltaic array was about two hundred feet from
a bore hole and the battery bank was about one hundred
feet below the surface along with the seismic monitoring
We recommended that they re-wire the photovoltaic array
in series/parallel and put an MPPT charge controller next
to the batteries.
Yup, it worked.
Another very important concern is shading of the solar
A number of years ago I was re-working a system that
someone else had installed in a commercial nursery.
I asked folks to move some trees in planters away from
Much of the day the trees cast shadows on the pv modules.
The customer did not think that would make a big difference.
The trees were moved and I put a clamp-on amp meter on
the array output cable.
While he was watching the display on the meter I tossed a
business card on one of the panels.
That took care of convincing him.
One of our systems, 48 volt, will have three sets of arrays.
Each set will consist of four Evergreen 115 watt ribbon
The four panels will be wired in series in a combiner box
on the roof for a nominal array voltage of 48 volts.
As of today, I have one of the arrays up and running - I hope
to finish this system before I need a walker.
Each array will have its own charge controller.
The first array gets good sunshine throughout the year.
The other two will have some shading in the winter due to
trees on the parkway which can not be removed.
This way the battery bank will get the most power available
Whenever possible, have your panels facing True South.
If you have a pole or ground mount this is much easier
than with a roof mount installation.
You can use a compass along with a map of your area
showing the degrees of declination for your area.
This will allow you to take the compass reading and adjust
for the difference between Magnetic South, which your
compass shows and True South.
The closer your panels face to True South, the more power
they will produce.
Panel Angle Tilt :
The angle of your photovoltaic modules have a definite
effect on power output.
In a perfect world they would always be perpendicular to
the sun - directly facing the sun.
As the seasons change the sun is higher in the horizon
in the summer than in the winter.
The ideal set up is one where you can change the tilt
angle of your panels throughout the year - lower in the
winter than in the summer.
On a roof mount installation this is not practical.
However on a ground or pole mount, this can make a
great deal of difference in the power output of the system.
Most pole mount systems allow "seasonal adjustments"
to the angle of your array.
Some ground mount setups have a notched or slotted
base which allow the rear vertical members to slide back
and forth changing the tilt of the panels.
On a fixed angle array the old rule of thumb is to take
your latitude and add fifteen degrees to it for the angle
of your array.
This is a sorta of happy medium for use throughout the
There is a simple way for aiming your panels.
This also works well for making seasonal adjustments.
Take a flat piece of metal or plastic and attach it to one
of the panel frames or the mounting rack.
Have it so it runs parallel to the panel.
Put a screw or pin in it perpendicular to the face of the
This way, when the rack is moved it will cast a shadow.
Around noon, adjust the array so the shadow dissapears -
then your panels will be facing directly towards the sun.
A note regarding recreational vehicles.
I have heard people say that having pv panels flat on the
roof is the best of all worlds.
Well, I have a full head of hair, no aches or pains and am
twenty years old.
Do not believe any of the above.
A flat mounted panel will never get near its rated output
unless the sun is directly overhead.